Type L is widely used in CA, unless City of LA has its own spec. requiring K.
Sch. 40 PVC is widely used also, and is generally reliable, but occasionally there something can happen. As you know, the pipe is not deep, so there is some vulnerability.
No problem with copper underground. It needs to be sleeved with a few wraps of 20mil pipe wrap tape as it come out of the ground.