|Posted by hj on May 20, 2004 at 11:01:18:|
|In response to Re: Propane to NG|
NG is regulated to about 6" w.c. LP is regulated to between 11" and 14" w.c.
: I have been working on NG systems for over 20 years and have never had to deal with a propane system. I would sub-contract the plumber to install the system and have the propane company drop the tank and regulator and do the final connection. I know residential NG is regulated to 14" WC or about 1/2 PSI, but what is propane regulated to? I wanted to know if I designed the system for the BTU requirements of a NG service and the pressure of propane so I could realitively easily make the change down the road. Thanks for the info!!!
|Replies to this post|
|There are none.|