|Posted by ED on April 13, 2004 at 17:40:32:|
|In response to Re: Installing a new washer & dryer in a new location!|
Good suggestions by the others.
Th electrical would require a dedicated 20amp circuit with 12-2 w/g wiring and the dryer if electric, would require a 240V 30Amp circuit with 10-3 w/G wire. Do not use a GFI outlet for the washer. If you add another (receptacle) near a utility tub for example then yes, use a GFI outlet.
Consider using the newer stainless steel washer hoses especially since this washer will be located upstairs near a bedroom. You may also consider a lint trap for the washer outlet hose.
: : Thanks for your help.
: : Regards,
: I would strongly recommend hiring a legitimate LMP
: 1- a 2" waste is required not 11/2 PLUS venting
: 2- Proper venting for the drier
: 3- Providing free air for combustion if gas is used
: 4-A Possible a pan with a drain under the washer to help keep your insurance costs lower WHEN the washing machine floods over and flows three levels down
: 5- Installing and testing a gas line.
: 6-Provisions for a "suds pressure zone"
: 7- Return circulation of the hot water as now your possibly exceeding the 50 feet lenth.
: 8- Dedicated electrical circuits with possible GFI protection
: 9- A house keeping pad possibly with a flood drain and non absorbent/ fire proof flooring
|Replies to this post|
|There are none.|