|Posted by Deb on February 23, 2004 at 19:28:46:|
|In response to Re: 4 ft Toilet -to- stack max in Seattle? (one more thing)|
: : Thanks Terry. I forgot to add that the new line would have to take a 45 deg bend at mid-run to the stack. Does this change the venting requirement?
: No. I take it that the neighborhood contractor is not a plumbing contractor?
: It's 6 feet for a 3"
UPC limits the length of a toilet trap arm to 6'--even if you run 4".
|Replies to this post|
|There are none.|