|Posted by john lerch on January 31, 2004 at 12:40:11:|
I have a Wilkins 600 pressure regulator on the main line into my house. Feed pressure varies around 80 pounds, and I want 60 pounds in the house.
The valve was installed around 8 years ago and has worked fine. Recently, however, we noticed that the house pressure was up significantly. The gauge at the valve showed 80 pounds. I purchased a new gauge, and it shows 80 pounds. I tried to adjust the valve, but it is unresponsive.
Is it possible that a seal or gasket has failed? Is there a rebuild kit, or do I need to replace the valve?
|Replies to this post|