|Posted by Eric on January 02, 2004 at 09:32:37:|
I recently had a new circulator pump and pressure relief valve replaced on my boiler. Now the pressure in the boiler is running high (32 to 34 psi) and is causing the relief valve to open. Is my inflow regulator (TACO 329) failing and allowing too much pressure into the boiler? Can the TACO valve be adjusted with the nut on top of it?
|Replies to this post|
|There are none.|