|Posted by Gary Slusser on December 27, 2003 at 11:40:15:|
|In response to Re: Well system water pressure falling off|
: Merry Christmas, Gary! I did get a kick on the trickleometer!
: We get the 'extremely low volume' when the pressure gauge is on the low end. Once the gauge reaches 48 psi, the pump kicks on and we will get water pressure back. With the old tank, we had a LOT more volume on the low end.
: According to the manufacturer, the water capacity of the new tank is 35 gal, but the drawdown at 40-60 psi (I'm at 48-74 psi) is 9.3 gal.
: I don't know the size of the old galvanized tank - the info plate was badly corroded - but it stood about four feet tall and had a picture showing a "Merrilfloat" (sp?) on the side. I have pictures of the old and new setups, if that would help.
: Should I look at bringing the pump 'on' pressure up?
: Thanks again!
Your trickleometer is working just fine. :) but what you need to do is reduce the pressure settings on the switch to 40/60 and the air to 39-38 psi with no air in the tank so the drawdown is greater and less likely to be as noticeable. IMO 30/50 would be even better, but.... you could have some restriction from the new plumbing you've done putting in the new tank. maybe a valve not fully open although it seems to be; gate valves are famous for that.
Otherwise, I'm out of ideas.
|Replies to this post|