|Posted by hj on July 21, 2003 at 09:34:21:|
|In response to Re: hot water heater pressure relief plumbing|
It has to be copper and cannot be "trapped" by going upward after leaving the relief valve.
: I am adding on to my house, and I need to move the pressure relief line.
: Do you guys know if this can be changed to PVC, or does it have to remain copper ?
|Replies to this post|
|There are none.|