|Posted by Barry on December 10, 2002 at 17:43:38:|
A friend has a standard two pipe vented heating system installed in a four bed two storey house in the 60's.
It has been extended in a bad way and there are now radiators off radiators off radiators all off 15mm pipes. Thus the last few radiators bairly get warm.
I realise that the best option would be to re-pipe with some 22mm ring, but that isnt an option at the moment. I was wondering about tying a "bodge" of putting another pump half way around the system to give it a boost. i ca see that the two pipes might conflict.
Anyone got any thoughts or suggestions ?
|Replies to this post|
|There are none.|