|Posted by Gary on August 15, 2002 at 19:05:31:|
|In response to Re: VENTING OF GAS WATER HEATER|
The "rule of thumb" is a horizontal run of 3 feet requires a verticle run of 3 feet,,,or H 5' V 5'.
Once you reach the outside wall it needs to vent up 2' above the eve of structure,,,this will enable it to draft,,,if you cannot get it to draft in the open air,,,I agree, better off not doing it, unless it's a power/direct vent.
Unless it is a direct vent heater designed for side wall venting, the major requirement is that you don't do it. Otherwise follow the heater installation instructions.
: : WHAT ARE REQUIRMENTS TO VENT WATER HEATER ON SIDEWALL?
|Replies to this post|