|Posted by dick on April 27, 19100 at 10:18:07:|
|In response to Re: Gas line and electric outlet|
I don't know what the regulations are, but.....
Don't bury soft flexible copper at any depth. it is too easily damaged and buried lines should be permanent. Use black iron pipe and bury it at least 2 feet deep. 1/2" pipe is plenty big for this. bring the pipe up at or near your grill and install a shut off valve. from the shut off valve to the grill use 3/8 od minimum soft copper or a gas rated flex line. If this last run is more than a couple of feet use 1/2" od line.
: Also, would 5/8" copper tubing (buried 12") be the best, or a plastic coated fuel line? (The grill is 40 000 BTU).
|Replies to this post|
|There are none.|