|Posted by Louie on February 15, 2002 at 09:46:28:|
|In response to Re: furnace expansion tank replacement|
It seems like your expansion tank is too small for the job. You need to know the total system water volume: Boiler+pipe size+length. (eg. the volume for each 100 foot of 1" pipe is 4 gallons). Once you know the volume (eg. 10 gallons) then go to the plumbing store and ask a 10 gallon expansion tank.
|Replies to this post|
|There are none.|