|Posted by CM on January 31, 19101 at 20:20:04:|
|In response to Re: toilet siphoning from one and the other|
If I understand your layout and you have the two WC's connected in a "Y" arrangement to a common waste line, putting a vent downstream of the Y connection won't help. You need a vent in each leg before they connect together.
: I have two toilets (with Sloan Flushmasters in them) that are next to each other and connect into a double elbow. When one is flushed it siphons the water out of the bowl in the other. I tried putting in a vent pipe right after the turn, it didn't help. Anyone have an idea?