If the tank was just outside the well you might get away with it. 32' is a long way for the tank to be from the switch. Still could be problems with the tank itself. Is it a fiberglass tank or steel? Is the tank vertical or horizontal? Fiberglass tank installed horizontal is no good. If the tank is good, you might make it work by using a pressure snubber (like Ray Roberts snubber) and water hammer arrestor tank (size of baseball) before the pressure switch.