Pull the handle off and move the stop tab.
Its a new install and I know the tankless water heater that supplies that shower will get so hot you can't put your hand under it. However, in the shower, the handle goes all the way to the left and the water is hot, but not hot enough. Guests have complained and I think its a problem. The little white 'inner gear' has a 'tab' on it that is situated at 12 oclock. IS this the adjuster? If so, what's the process? Moen website and manual only tell me how to go COLDER from there...not what I need.
I did. That's the max. I actaully took it out altogether and the handle moves no further. I guess my faucet that is marked at 2.5GPM is not the same as my shower marked at 2.5GPM. Shower must be closer to 2.5 GPM and the faucet must be closer to 1.5-2, because it gets screaming hot. Shower gets barely over 100. Guess the tankless heater is too small.
Just choked the water down at the water heater. It's better, but not stellar.
Last edited by jed1154; 12-08-2013 at 11:25 AM.
What size and type of tankless unit? What is your incoming cold water temperature? What you're seeing seems typical of an undersized tankless. Or, you're trying to use an older showerhead that uses more water than the new regulations mandate (or you drilled out or removed the restrictor). You may find that just picking up a low-flow showerhead may resolve your issue.
Important note - I'm not a pro
Retired Defense Industry Engineer; Schluter 2.5-day Workshop Completed 2013
Its a 14kw heater. My water temp coming in is about 65-70, and at 2.5gpm, the label on the heater says 38* rise, which is consistent with what I am seeing in the shower. The shower heads are NEW. Do they make some that use less than 2.5GPM? That doesnt really help the spigot. If I had known that, I would have installed one of those moen valves that lets you adjust the water blend separate from the water pressure....that would have been sweet. Oh well. Any other easy solutions?
I have multiple tankless heaters, all are small ones. I have a 12KW, a 14kw, and a 15KW. The 12kw serves a shower in another part of the house, and by god you can peel your skin off if you arent careful. My 15kw will do likewise. No clue why the 14kw can't keep up. Very odd, different electronics I guess.
Last edited by jed1154; 12-08-2013 at 07:39 PM.
Last edited by MikeQ; 12-16-2013 at 05:49 AM.