It should be a double fixture fitting. A double wye creates a double S trap. A double fixture fitting is made so that air in the trap arm meets the stack before the drain drops down so that a siphon cannot be created. If the trap siphons it breaks the trap seal and there is nothing between your nose and whatever gas is in the sewer. An exhaust fan in the bathroom makes the situation worse.