If you have a 15 ohm bleeder resistor, then that sounds wrong.
Your description of 155.5uf has me a bit confused, if it should be a 40uf cap. I may have misunderstood.
Does the Breaker trip, just as soon as it starts or tries to run, or is there a delay before it trips ?
You should have no continuity from the compressor frame to the start and run windings, when the compressor is disconnected.
What Model are you working with ?