You are under UPC plumbing code.
The double lav needs to be a double fixture fitting, and you can use med 90's on the trap arms. Long sweep would work too there.
You do have a long sweep below, and that's correct.
4" allows pretty much as many toilets as you like.
I don't understand how the lav vents are tying in. It should be above 42".