The trap arm nust be vented within 42" on 1.5" pipe, and not below the trap arm. If you put a bend in there, it becomes an S trap that siphons the trap dry.
I believe that 30" is the max you can go with an arm to the second bowl.
You also have way too many bends there. Have you considered pulling drywall off and putting real plumbing in the wall?