Originally Posted by hj
If you are lucky, the feed could go to the GFCI receptacle first and then to the switch. If so, all you would have to do is change the wire from the line side to the load side.
I got into the property today. The vanity receptacle and the lights are on two different circuits, the vanity conduit passes nowhere near the light switch.