You have also altered the height of the shower drain, making is an ilegal S trap.
I see too where you have the tub draining past the shower, which will siphon the shower trap.
Also, you have a santee on it's side. At the least it should have been a wye fitting.
Is any of this vented?
So much wrong, in so little space.