The 20 amp breaker is OK. I would have used at least a 15 amp breaker anyway. That old of a motor I don't believe has an overload built into it. So there should be an overload the right size built into the control box. If the control box has ever been changed, you need to make sure you use one that has a built in overload. Probably a loose connection that caused the wires to melt.