There is some kind of problem. Black to red should be 240.. You are good at the box and not out at the load.
There are too many questions here....you need an electrician. We don't know why there is a white lead out there. Pure 240 loads are 2 hots and the ground, so you have some 120 going on. Don't get hurt...get help!