I've added a 100 amp Sq D subpanel off of a Seimens 200 amp service. The cable I used has 4 wires (1 black - hot, 1 red & black - hot, 1 black & white - neutrel and a ground). My question is where these wires go into the 200 amp service. I'm assuming the following:
1) The 2 hots get connected to the 100 amp breaker in the main panel.
2) The black & white gets connected to the left side of the panel on the neutral side
3) The ground gets connected to the ground bar on the right side
*** I've attached pics of both the sub and main panels***