Seahawk Highlights Video (206) 949-5683, Top Rated Plumber, Seattle

# Thread: Voltage drop in underground cable

1. ## Voltage drop in underground cable

I have a problem with the underground wire feeding my cabana I run a 110 volt pump to water my lawn as I am on a river ,I have done this for the past twenty years . This year I plugged in the pump and nothing so I removed the gfi receptical and put my tester on the wires comming out of the ground and got a reading of 62 volts. I then went to the panel and tested from the breker to neutral and got 120 volts.I am wondering if maybe something has bitten through the neutral wire ? Is this possible I would appreciate any advice you can give thanx in advance Fred

2. A loose or corroded connection anywhere on the run might show up as a low voltage at the end. Does the cable have a ground wire? What's the voltage between hot and ground?

3. My bet would be a break in the wire underground somewhere.

4. Originally Posted by jadnashua
A loose or corroded connection anywhere on the run might show up as a low voltage at the end. Does the cable have a ground wire? What's the voltage between hot and ground?
yes it does have a ground wire and the voltage between hot and ground is the same 62 volts

5. A high resistance on the feed would result in a voltage drop that is commensurate with the current draw. A high impedance voltmeter testing a circuit that is not under load usually does not give a true picture since it in and of itself, provides no current draw.

My guess is that along with the high resistance, there is also a short to ground.

6. quote; yes it does have a ground wire and the voltage between hot and ground is the same 62 volts

That would imply a problem with the "hot' wire, not the neutral.

7. Originally Posted by LLigetfa
My guess is that along with the high resistance, there is also a short to ground.
I don't think that is correct.

hj is correct.

A short reading from Ground to Neutral is normal, at the source.

The open is on the Hot leg, if there is a open.

Or if the pump is trying to run, it may be locked up and not running. that could explain the voltage drop.

You can use a light bulb for better testing under a small load.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•