You are using a Cycle Stop Valve, so you don't need torque arrestors or cable guards. Those things only help when you have a pump that is cycling excessively, which won't be the case when using the CSV. Torque arrestors and cable guards are just something to get stuck in the well, and will make it harder to pull.
Yes you can use the SS cable to pull the pump, but that cable is again just something else down the well that can cause problems. If you drop or break that cable, it will wedge your pump in the hole and you will need to drill a new well. Better off just using 160# poly pipe and pulling the pump with the pipe. With a static of 36', the pump will nearly float out anyway. You will probably almost have to push it down to get it in the well.