To determine what is going on in a heat pump system, you first need to determing your subcooling number. 250 PSI correlates to about 117º. Now MEASURE the temp of the liquid line, and the difference is subcooling. A spec chart for your unit should tell you. I don't know the number for 15 ton units.
Freezing can indicate undercharged, but also can indicate a restriction.