Don't use a rubber fernco use one of these.
I'm adding a lav and a shower midway through the run of my main under slab. Routing and venting are all addressed and to code. My question is what is the proper way to cut into the main and add in my wye fittings when I do not have any end movement to get the pieces all back together. I do not have enough movement sideways in the main pipe to move it aside to squeeze in the last fitting. I guess I can cut the pipe a little shorter then add in a rubber coupling at the end????
Plumbers would have cut the fittings in FIRST, and then worked from there to the new location.