I want to install a single light in our crawl space with a switch near the access door. I want to tap into a line feeding a receptacle to the room just above the crawl space. The circuit is 20amp/#12Guage. Is it allowable to run a #14G leg off that circuit for the new light?
Thanks for any advice.