in january i was promoted to a apprentice election and i am in my 2nd class residential wiring 2 at the school.my work started me late ( with the school class schedule) so i missed the code book class and i will take it in the fall.
i have been tring to understand the code book by looking up codes and thinking of questions and finding the answers and i found a question that i can not find the answer that was given to me in school.
#1. i am told by everyone that you can not put romex in coduit for a continous run,because of heat and #2. you can not put 1 raceway inside of another . ( i can not find these 2 things spelled out in the nec book)
i found you can run it inside conduit for protection of nonmetallic cable in a basement. nec 300.15(c) nec 334.15(b)
i know i have missed something
i want to understand how i should be reading or understanding what i have read to make it make sence . if that makes sence .
any help would be greatly appreciated
thanks in advance.