I have a hydronic in floor system. I have only had to purge the air only when I made some changes. I suspect that if you shut off the flow on the zones that are flowing and open the drains it will eventually purge tha air bubble. I had a DIY towel warmer and it took about 15 minutes to get all the air out of that sucker. I think you need to be more patient and it should work out.