Air in the system would be my first guess and the saddle valve was a bad idea. The air needs to be purged at the boiler. There should be a purge valve somewere near it. Second choice would be a bad circulator. If you have zone valves and one went bad you would have no heat in that pipe at all. Third choice is all electrical. Either thermostat or zone control relay.