I was checking my well pump pressure switch to determine if it could also control a booster pump.
I found out that the switch was cross wired wrong,that is when the pump is off the motor terminals have 230 volts and lines 1 and 2have zero volts.
Since the well has operated that way for 10 years I beleive that the pump starter control input was also crossed to undo the mistake.
Is it ok to leave it as is? Does this affect the contact points?
Thank you in advance for any info.