Basic electric service panel questions
I'm having a home inspection this weekend on the house I'm selling and I'm a little concerned about the electrical inspection.
A couple quick questions:
1) For a 200 amp service, you draw 200 amps from each leg, right?
2) Is it a problem (does code require) that the breakers on each leg total to less than 200? Or is it only necessary that the actual load being drawn be less than 200 amps? I have a total of 230 amps of breakers on one leg and 200 on the other.
Will this be a problem?