NExt question, hope someone is still out there...
HJ, thanks and it does test right.
Originally Posted by hj
DonL, thanks for coming back after my little rant. I do appreciate the help. I'm ignorant, not stupid...And yes, that blob is a fan. Circuit is designed to open a damper and turn on fan when switch is pushed, from both bathrooms as well, without sending 240 volts to the fan. the electrician helped me design it so the same power is going to the fan when both circuits are open.
1) Could I have fried my timer switched doing ti the first diagram? I can't get them to function properly. When I use them in the circuit, they close immediately. (If someone would like to help me troubleshoot these switches, I'd take that help also)...anyway...
2) Can anyone tell me if it's possible to add another timer switch to trip the relay from one bathroom? I have the switch in the toilet room, but would like to put one out in the bathroom proper if possible, so i don't have to go in the toilet room every time I want to turn it on. Is it as simple as what I put in the drawing?
(I have changed the drawing to more accurately reflect the way it will be done. I started to use red for the SWITCHED power, just to make it easier to follow). Thanks for any and all help!!