Can you tolerate ONE More question about Sub-Panel?
I am in the process of installing a subpanel in a separate basement storage room. The proper size wire will run through a wall and about 30' from the main panel. This is the FIRST subpanel from the main box.
I plan to run Three single conductor wires from the main Panel to the sub and connect all the neutrals on the neutral bar. I will have to buy a separate bar for the ground and connect them.
I then plan to drive a new ground rod into the ground and run the wire to the new grounding bar and install the bonding screw.
Is this correct?