Wall Window A/C Condensation Doesn't Drain
I'm not sure if this is the right forum to post this, but I've had luck here before so here goes: my wall air conditioner does not drain the condensation at all. Somehow it got clogged. It's a small unit, Maytag/Fedders m6x06f2a, and only cools our 10x12 room. Any general ideas on how to "unclog" it? Thank you.
Fedders Large Wall A/C Drain problem
I found a 2007 model large wall unit with a drain design problem. Drains were all clear but this unit with its powerful blower sucked up the water from the drain pan and blew it into the room. Standing in front was like taking a shower. We designed a drift eliminator by covering the lower section of the coil and drain pan and keeping that section isolated from the fan's negative return air pull. Works great. All water flows outside now.
Sal Castro, P.E.