View Full Version : Hot water at cold side all faucets
06-21-2010, 04:57 PM
I have a home in Chicago that has hot water to all faucets on cold side. There are Grohe thermostatic valves at all showers (4). Only recent work was a new water heater 3 months ago. I am at a loss any help would be appriciated! Thanks in advance!
06-21-2010, 06:43 PM
Were they normal at some point? If just one of those faucets was failing there could be a potential cross connection. I have seen a couple of occassions where this has happened, but it has usually been with a cheap brand faucet.
06-21-2010, 07:59 PM
Or more likely eather the water heater was hook up wrong i have seen even professional
plumbers do this !
Or you could be missing the dip tube ?
If this problem started about same time as wtr/htr was changed out that is where you
need to start looking !
06-21-2010, 08:03 PM
Check your messages on your profile page ! ! !
Reversing the connections to a water heater does NOT change the hot/cold orientation of the faucets. ALL it does is reduce the amount of hot water available. Changing hot to cold, and vice versa, requires a piping change somewhere.
06-22-2010, 07:32 AM
Do you have any kind of recirulating system? A failed check valve or improperly installed system could be a problem. If you have a retrofit recir, then warm to hot at the cold tap is a normal side effect. If you run a cold tap for a few minutes, does it turn cold, or stay hot?
06-22-2010, 12:17 PM
Thanks for the replies. There is not a recirc line, and the water heater was replaced 3 months ago and worked fine untill three days ago. I think that the check valves in one of the Grohe thermostatic mixing valve hav gone bad allowing the water to pass? They are all about 4 years old. I have read that the washing machine selonoid gould also be bad. I will look further into this, and hape to find a resolution to it.
The water will eventually get "cold", but stays warm for a while!
Washing machine solenoid valves CANNOT cause the problem, regardless of what you have heard.